Aberdeen, MD Air Conditioning, Heating and Plumbing Services
Supreme Service Today provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Aberdeen, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Service Today.
for Aberdeen, MD
Main break next to meter Dug up next to meter found cracked quest coupling replaced ten ft of poly and used ford couplings Back filled to grade Collected cash for remaining balance Need to call county to turn on meter
Sold estimate for spot repair on water main collected $1,000 in cash for deposit
Upon my arrival I found unit operating with 0 td across the evaporator coil. Outdoor fan motor was operating. Access to the condenser units electrical panel was extremely difficult and required me crawling under the deck, laying on my stomach and working with my arms reached awkwardly into the electrical cabinet. The voltage absorption system for the fan motor was up to spec but the separate voltage absorption system for the compressor had failed. I called the owner and was given approval to do the repair quoted plus dispatch fee. I crawled back under the deck and replaced the 35uf run capacitor and secured the cabinet door and screwed on two valve caps. I started the unit and had 85 return with 64 supply. The unit is under a heavy load pressures would not mean anything given the extreme load but given that the unit has 21 td shows that it is operating normal.
Tuneup on 06/27/19 on arrival set unit to call for cooling measured supply and return air temp no DT checked electrical connections checked voltage and amps checked condenser drain and cleaned checked filter is cleaned checked condenser coil outdoor the condenser fan is not running checked compressor capacitor I put new capacitor and checked is not running I explained the customer I gave quote for condenser fan motor and fan motor blade also capacitor replacements he is going to call us when his ready I take out the capacitor I put I collected $59 for tuneup special. Unit is not operating normal at this time I disconnect condenser unit outdoor from the disconnect box.
On arrival found thermostat satisfied at 69 ,found filter very dirty ,removed it and advised tenant to get new filter .closed couple vents in the basement.noticed more air flowing to upstairs.checked system pressures.found pressure ok .also noticed outdoor unit has no access to service panel and also starving for air flow .called landlord but no answer . Unit is operating normal at this time
Replaced round front toilet on second floor master bath , tested no leaks , Donna will call customer for payment
Customer has leak on fluidmaster will discuss with husband and call back in to inform us wether we are repairing or replacing to toilet.