Abingdon, MD Air Conditioning, Heating and Plumbing Services
Supreme Service Today provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Abingdon, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Service Today.
for Abingdon, MD
Great friendly Service
Effie - Abingdon, MD
Technician was very knowledgeable
Richard - Abingdon, MD
Being someone who has worked serving customers for over 50 years, I am pleasantly impressed with the service provided by Matt, Edruado and Mark. From the beginning this whole Leak problem was a pain. Mark provided a solution that three other plumbers wanted nothing to do with. Matt implement ed
Prompt courteous service
Lauren - Abingdon, MD
Technician was friendly, knowledgeable and prompt!
Adam - Abingdon, MD
Quick, clean and honest!
Spickler - Abingdon, MD
Quick and courteous! Fixed the issue very quickly, and explained everything in detail. Very happy. I can't thank you enough!
Arrived to inspect unit making loud noise. Inspected system in heat test mode and ac test mode verified proper operations. Found problem due to blocked up filter. When air passed blocked filter causing a humming sound. Changed filter with one the customer provided and noise has stoped. unit now running properly after changing filter
Came out to replace two faucets and connect pop up assemblies. Replaced cartridge on faucet in the middle of hall upstairs. Also tightened the bolts a hair on toilet and screws were loose on seat so I tightened them up as well.
Return visit on 12/27/19 On arrival take the old surface ignitor out installed new surface ignitor in tested start up and unit began operating very smoothly without any hesitating or lag checked electrical connections checked voltage and amps checked blower capacitor checked coil checked blower motor checked air filter checked drain line measured supply and return air temp DT 47.5 temperature rise made for 40 to 70 unit operating normal at this time. No payment collected is full paid.
Service call on 12/26/19 On arrival set unit to call for heat inducer comes on and the gas valve is open but the ignitor is not lights up also I have error codes 34 flash ignition failure I take the ignitor out I found is cracked I suggested to replace it now to furnace operating I gave quote for customer also customer she got special discount by Alex customer accepted the quote the ignitor I had is not fitted to the furnace I ordered the parts we have to come back to finish the job customer schedule for tomorrow morning between 8 to 12 Customer also sign new service agreement I collected full of the job balance $239.51 on C.C HOT SURFACE IGNITOR REPLACEMENT ALSO NEW SA
Installed power vent water heater, ran drip pan to sump pump , strapped up and adjusted grade on vent , put silicone around vent where penetrates exterior wall
Cleaned up yard ,put split rings on main and put concrete in the hole
Will relocate water service on the inside of the house. Will bring 1 inch black polybutylene to back corner of living room lead up the wall secure it it go through wall to bulk head on other side of partioned wall. Follow down that bulk head till you reach where old service is at and tie back in. Eliminate old connection from old incoming service in water heater room and then cap off. Will also refer a company to bulk head out the pipes to hide the better. Bulkhead , drywall, framing, painting needed to concealed or repairs drywall as part of water main replacement by others
Will relocate water service on the inside of the house. Will bring 3/4 inch black poly to back corner of living room lead up the wall secure it it go through wall to bulk head on other side of partioned wall. Follow down that bulk head till you reach where old service is at and tie back in. Eliminate old connection from old incoming service in water heater room and then cap off. Will also refer a company to bulk head out the pipes to hide the better. Bulkhead , drywall, framing, painting needed to concealed or repairs drywall as part of water main replacement by others
Up on arrival for no heat call found system is not working. Found air handler pen is full of water do to secondary drain line from secondary heating exchanger was not connected to the unit. Installed drain line back to the system. Sucked all the water from air handler pen with shop vac . System operating normal at this time .
Will relocate water service on the inside of the house. Will bring 1 inch black polybutylene to back corner of living room lead up the wall secure it it go through wall to bulk head on other side of partioned wall. Follow down that bulk head till you reach where old service is at and tie back in. Eliminate old connection from old incoming service in water heater room and then cap off. Will also refer a company to bulk head out the pipes to hide the better.
Upon arrival for fall p.m 10/30/19 I notice furnace was to small for this home. I noticed the return air duct was too small for the furnace this furnace is 10 years old Iâ€™ve done inspection on heater Exchanger notice hairline cracks possible, carbon monoxide could be leaking from furnace. I gave Alex a call to explain what I found During my fall Pm Inspection alex advise me to give the customer a call to set up a Confort advisor to come out for options of replacement. at this time Iâ€™m going to tag furnace shut off gas shut off power to furnace. I explain to customer before I leave Iâ€™ll make a note of everything taken pictures. Iâ€™m not responsible for anything that happens once i leave the property.
Upon arrival customer explained to me duct main track line and around ask all condensating throughout the ceiling in living room dining room area. watermarks on ceiling due to duct work condensating. I gave Alex a call to explain in detail whatâ€™s going on and how to price out job. Rapping duck work throughout first floor level main trunk line is 15 foot long, One round duct tee off 10 foot lenth the other round duct T off 5ft & another one 5ft in length 3ft in lenth T off 4ft in lenth & one round duct T off 3ft length
Returned to install kitchen faucet and eliminate garbage disposal and tie sink back in. Tested and works perfect.
Installed new power vent water heater. Tested and works perfect. Connected to existing connections. Took pictures when I was done.
Paid trip fee 49.00 for trip will have to work up the funds before we can do job for customer. But offered to deduct trip from job balance when customer decides to schedule the water heater replacement.
Upon arrival found indoor running and calling for cooling but outdoor unit not running. Found issue with repairs preformed in May this year, resolved issues with Denny and fixed repairs under warranty to customer. System still did not come on. Traced issue to control voltage being cut off. Hooked up gauges and found system is flat on charge. Quoted basic no braze repair of leak but informed customer how price can change based off where the leak is found. Customer approved work to be done and scheduled for Tuesday July 23. Customer also wants price to replace a/c system so she can have all options priced out before making decision on what to do, repair or replace. Comfort advisor also scheduled on Tuesday July 23.
Upon arrival found water all around system. Inspected condensate line and found most of it with water on the outside. Opened coil panel to inspect condensate pan, found coil frozen, filter at bottom of return box sitting in about an inch and a half to 2 inches of water. Unable to diagnose due to frozen coil, advised customer to not run a/c system but is able to run fan to circulate air. Filter size is 20x20x1, also 16x16x1-3, customer will supply filter for visit tomorrow, scheduled follow up visit for tomorrow, July 2 from 12-4.
Upon arrival checked indoor system, found air temp difference only 6 degrees and excess condensation forming on insulated suction line. Also found blower capacitor out of spec. Inspecting outdoor unit found contactor very burnt and in need of replacement. While system running found 35 psi suction and line freezing at outdoor unit, head pressure also low. Advised leak search and repair on system, customer interested in replacing system since there is no guarantee of system health or longevity after repairs. System is 22 years old. While on site scheduled appointment for comfort advisor, scheduled Monday 5-7, so customer can see options and weigh is options.
Spring Pm On 06/28/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter cleaned checked condenser unit checked electrical connections checked compressor capacitor checked voltage and amps tested unit operating normal at this time. Highly recommended duct cleaning also blower needs to be cleaned.
On arrival found outside unit not operating,found bad compressor.also Contactor is burnt in addition to ,customer informed me that unit has history of a leak but previous company couldn't find it .checked standing pressure which was slightly low .recommeded leak search .custmer declined repair at this time .
The thermostat displayed no 24volts power from the furnace. I went into the attic and the furnace door had not been latched back correctly and it had separated from the furnace several inches allowing it the door switch to open. I replaced the door making sure it fit and secured correctly. As soon as the furnace door was properly secured the blower began operating. I went to the condenser to make sure it was working.
Spring Pm On 06/17/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter recommended replaced air filter checked condenser unit outdoor checked electrical connections checked compressor capacitor checked pressure and temp zero leaks checked all electrical connections units operating normal at this time.
On arrival found system low on refrigerant (410). Informed customer that system has a leak ,custmer preferred to recharge it at this time .added 1.5 lbs of 410 a .subcool 10 and supreheat 11 .unit operating normal at this time.
Upon arrival, stystem cooling properly, working properly, found blower cap and run cap outdoor weak, customer approved work and signed up for service agreement. Replace and working properly now.
FOUND THE REFRIGERATE LEAK ON THE HIGH SIDE SRATOR VALVE. REPAIRED AND CHARGED THE SYSTEM. CHECKED OPERATION.
On arrival found pan full of water and dirty filter. I replaced filter.Measured return and supply and I was only getting 2 degrees differential. I removed wet switch from the pan and I noticed my delta T started to changed. Return 80 and supply 68. I put my gauges on and my super heat was high and sub cool was low. I did I leak search but I wasnâ€™t able to find the leak. Customer want us to comeback and do a nitrogen leak search. Customer stated that we have a credit card on file, we have been charging it for years. Leak search + todayâ€™s trip fee needs to be charge. Custumer want us to comeback on Monday. She will be home all day.
Replace voltage absorption system, voltage distribution system and install a hard start kit.
I replaced the air filter with one provided by the customer. I cleaned the condensate drain line and ran water to flush out any debris and to make sure it drained properly without leaks. Unit cooling with 20+ degree delta temperatures across the evaporator coil. Refrigerant pressures and measurements were normal, no evidence of loss of charge from a leak. I checked the electrical wiring and electrical systems, and found 2 main components at the condenser that need to be replaced. I showed the customer and also recommended adding a hard start kit. The unit is operating normal, with electrical repairs needed to keep the system running.
Replaced Outdoor Fan Motor and module. Power was shut off when I arrived. Removed old mounting and then removed motor from mount and blade from motor. Installed new motor with reused blade and mounting brackets. Verified tight connections and returned power to system. Customers brother came and let me in house to test unit. Ran ac and checked operation. Outdoor fan running normally with compressor. Measured amp draw of both then took temperature readings at both coil. Found normal heat rejection outdoor and normal delta air temp indoor. Unit is operating normal at this time. **Still need to collect balance from customer. Paid me $300 cash as a deposit for part last visit.**
Upon arrival I was told that ac wasnâ€™t blowing cold air and outdoor fan not running. During diagnostics I found compressor running but outdoor fan not. Removed molex plug from motor and found it is getting both 240v and 24v, Motor should be running. Shut off power and ohmed out coil and found no ohms, winding broken. Quoting customer to replace Outdoor fan motor. Customer approved and paid deposit of $300 (cash) so we can order motor. Office please follow up with customer on part arrival. He would like to schedule return trip for Monday after 3pm if possible.
Invoice created to clear up AR
Secure shower diverter and tub spout both are loose and not sealed against shower wall causing water to leak behind shower
Raise pipe in mechanical room install clean out above flood level water is coming out of open sewer pipe onto floor due to it being open below flood level
Cable main sewer line to clear blockage
Upon arrival I found thermostat in off position because customer said unit was blowing too much cold air. During diagnostics I called for 10 degrees of heat. Unit was running 2nd stage heat but aux not running. Found AHU fault Ec which states an unmatched aux heater kit. Found Board was setup for 20kw when heater kit in unit is only 10kw. Changed dip switch settings and reset power. Ran aux heat and checked amperage. Ran HeatPump and aux heat together and checked operation. Unit is operating normal at this time.
Replace 40 gallon gas water heater also needs ball valve expansion tank and drain pan customer also wants water heater raised up off the floor dues to flooding issues. Remove nipple on gas line and install shorter nipple to accommodate raising water heater
I replaced the filter indoors and went on the roof to check the operation of the unit in heat mode. I found manifold gas pressure was a little low at 2.5, which I raised to 3.5 iwc. Unit had a temperature rise within printed range. I checked the electrical wiring and electrical systems. The safety devices for the gas furnace are intact and operable but weâ€™re not tripped or engaged during a call for heat. Control board also indicated normal operation. The unit is operating normal.
Install new diverters in upstairs bathrooms
Cutomer approved installation on 3/4â€ PE water main
Tune Up on 12/13/18 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter recommended to replace the air filter Avery 90days also highly recommended to install UV Lights also customer complain about air filter ruck is to hard to access customer need some one come out check it for him unit operating normal at this time.
On arrival removed flame sensor i then installed new flame sensor.tested unit ,unit operating normal
Fall pm on 11/30/18 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters found for unit #1 in attic flame sensor is bad need to be replaced I gave the quote for customer.customer accepted I ordered the part we have to come back to replaced the part Monday @4:00pm we have to call the customer before 30min also we have to collect full amount of the repairs.
Started to do maintenance on unit . My supply temp got up to 223 degrees . Pulled off the top of the unit and found multiple cracks in heat exchanger. Wrote up a quote sheet to replace heat exchanger and inducer motor . Inducer motor is over amping rated for . 5 amps pulling 1.6 amps . Unit is 20 years old . Recommend having one of our sales guys to come out and give estimate for replacing entire unit .
Inspection on Trane furnace in Joppatown, MD .