Bel Air, MD Air Conditioning, Heating and Plumbing Services
Bel Air is located in Harford County, Maryland. Bel Air is located on US Route 1 and has a population of 10,120 according to the 2010 census. Bel Air’s summers are warm, humid, and wet, and the winters are cold and windy. Throughout the year, the temperature usually ranges from 26°F to 85°F and is rarely below 13°F or above 92°F.
Incorporated in 1874, Bel Air originally went by the name “Scott’s Old Fields.” With the introduction of the canning industry, the Ma & Pa railroad, and other financial businesses, Bel Air began to grow into the town it is today. Currently, Bel Air includes one of Maryland’s 24 designated Arts and Entertainment districts. It is used for concerts, art galleries, other venues and events, and it is located in the city’s downtown area. The town is also the center for governmental, educational, cultural, medical, and commercial institutions in the county.
Supreme Service Today provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Bel Air, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Service Today.
for Bel Air, MD
Marc is the epitome of great service. B
Stavrou - Bel Air, MD
We had a small issue after our newly installed ac and furnace unit were put in. Marc was on call that night and came up with a solution to our issue.
Joe did a great job today. Very helpful!
Jill - Bel Air, MD
Jill - Bel Air, MD
Super nice and friendly and helpful!!
Up on arrival for furnace not running call on 01/17/2020 found faulty gas valve , low blower motor capacitor, system was not installed properly, system not wired properly, needs breather flue pipe , space to small for space exhaust. Customer requests estimate for new system. ASAP
Fall pm on 01/10/20 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain checked air filter and replaced checked compressor capacitor checked coil checked blower checked electric heat checked EWP and LWP it was low I pump it back up 65/59 psi checked water temp checked all other electrical connections unit tested unit operating normal at this time. Recommended uv lights installation and Ez trap or wet switch installation also hole house surge protector to avoid future problems.
Hooked up two hose bibs ,replaced toilet, chipped wall and install new drain line for sump pump, also hung attic access step ladder Check water pressure for home and adjusted prv. 69 psi
Replace saddle valve and connect refrigerator. Will deduct evaluation fee from balance. Customers daughter wasnâ€™t here to approve of job just yet.
On arrival pumped system up to 50 psi .also checked system again ,found pitted Contactor .checked connections ,cap.recommended replacing Contactor but customer declined repair .unit is operating normal at this time .
Inspected geo system. Tested system in heat test mode to verify proper order of operations. Found unit to have low water psi. Needs to be pressurized and filled. Did not have fill tool onsite.
Upon my arrival I found all 3 thermostats were keeping set point of 72. I went into the clinic to get the doctors impressions of what was happening. I found the thermostat was reading 1 degree above room temperature so I set the offset to -1 degree. I raised the temperature by 2 degrees and went on the roof to check operation of RTU#3. Both compressors were running in heat mode and auxiliary heat was running all pulling normal amps. Once the auxiliary heat cycled off I checked temperature rise across the air coil in heat pump mode only and had 72.3 return and 106.7 supply, which is pretty much ideal. When I went back in I was talking with the doctor and they had a realization that the printer that is set beneath the thermostat puts off a lot of heat when printing and that could easily be throwing the thermostat off. I agree that this is a strong possibility and the printer can be more than easily moved than the thermostat. Unit operating normal.
Inspected units for fall maintenance inspected and documented and system operations. Replaced the filters. Found units to be running properly no issues found.
Inspected all systems for fall season maintenance. Inspected and documented all amp draws and voltage reading.inspected and changed all filters. Units all running properly no issues found.
Graded out yard Attempted to put Strahl down but the homeowner asked us not to add an expansion tank to water heater in basement patch concrete around Watermain and cleaned up some
Installed water service
Replace 60amp breaker in main electrical panel. I replaced the 60amp square d breaker in the main electrical panel and tested the unit for proper operation. Unit operating normal.
I pressurized the ground loop to 65psi standing pressure.
Replace water main line 1 1/4 comes in to the slab by the gas services will have to hand dig from shut off in yard then hammer drill through side wall.Will also install expansion tank on water heater. Paid 1425.00 for deposit for work to be done.
Inspected unit in heat test mode to verify proper operations. Inspected unit and found low water psi. Unit needs to be filled and pressurized. Return needed to fill.
Finish hooking up drain line from drain pan from newly installed water heater.
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical wires,filter,coils,caps,blower ,unit is operating normal. Customer was not home .
Installed water heater, did not have materials to run pan line someone needs to return to install pan line
Raheem marathon storage tank for the one that is leaking and connects to the drain-super heater lines on water heater. Will tie onto existing connections and test for leaks once installed.
Gave quote to fix blue poly main line. Requested to be followed back up with tomorrow to see if quoted work is excepted.collected 49$ trip fee.
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections inspected drain,coil,safeties ,heat exchanger.found blower motor leaking oil which is a sign of failure,i then informed customer and recommended replacing motor but customer informed me that she is selling the house .unit is operating normal
Up on arrival performed fall maintenance on 10/28/2019. Checked all thermostats, checked all units for operation. Took delta T on all units. Took readings on all electrical components. Unit working good at this time.
Extention ladder needs to be set up in back of store. Spoke with manager and went to roof. Wrote down model and serial as well as the filter and belt list for all equipment.
When I arrived I talked with customer about 20 year furnace and AC unit he asked if I can check the AC before I check the heat I gave six options estimates customer says it cost too much to put money into a 20 year old system customer is ready to replace but not sure if he wants geothermal or gas furnace with AC. Call dispatch Karen to set up a Confort advisor to come out next week Thursday to go over some options of replacement customer is interested in becoming a member customer paid $16.66 and will give application to Deny on Thursday.
Drains were semi clogged. Will clean and test. They were clogged right at the drain stop. After cleaning I tested and the drains were draining how they should. Hair was the problem with the drains being clogged.
Furnace fuse was blown. I found yellow wire for cooling was smashed by the condenser door and cut slightly. I called the installation manager for warranty approval. I routed control wiring correctly so that it cannot be pinched again by the condenser cover. I strapped up some loose wires and ran unit. Unit was only cooling with 10 degrees. I applied refrigerant gauges and had 40 degree superheat. I added just over a pound of refrigerant to get 6-8 degrees superheat, normal pressures and 20 degrees delta temperatures across the evaporator coil. Unit operating normal. 1lb of r410a refrigerant and some expendable supplies were used.
Water main is flooding front yard. Took pictures of outside. Will do a pull and bring in new water service to water meter.add in ball valves. Expansion tank also on water heater. 12 month interest free financing.
Up on arrival Replaced condenser fan motor capacitors on condenser units 1,3 and 4 . Checked units for operation. All units working good at this time
Up on arrival performed operational inspection maintenance. Changed all filters and tested all units for operation. Found units # 1,3,4 low capacitor, recommend to replace them. All units are working at this time.
Paid 900.00 when job was complete. We came out to install new water heater. We tied onto existing connections tested and customer now has regular pressure and hot water now.
Up on arrival performed operational inspection maintenance, checked all units for operation all units working good . Changed filter on all 3 roof top unitâ€™s. All units are working at this time.
Found pump to be inactive. Gave quote to replace well. I shot high Incase of possible pump price. Advised We would need to find out what the pump price is first before we can give a better number.
Came out and assessed water heater found water heater to be some what old no manufacturers date. Replace water heater that has a bad control board on water heater recommend this as the best option for customer due to age of water heater.
Service call on 09/18/19 On arrival set unit to call for cooling 7 to 9 DT checked electrical connections checked voltage and amps checked filter checked blower motor checked compressor capacitor checked pressure and temp I found is low on charge checked superheat is higher is normal checked all other electrical connections I gave quote for customer customer to leak search customer doesnâ€™t want the repair but customer needs estimate for replacement customer schedule for tomorrow between 9 to 10 am I collected $59 dispatch fee and $124 diagnostic fee total $183 on check #1529
Came out to look for leak in basement Could not find anything believe ground water is seeping up threw the slab near backwater valve for basement bath, did find broken hose bib near garage gave estimate
When I arrive and check thermostat lower the setpoint to 70 access the attic to check unit 30 minutes went by no short cycling unit and fan motor ran fine delta T 51Â° went out to outside unit everything is running fine pressures are all OK normal. I spoke with the homeowner and such a suggest that the thermostat nest be re-configure to this new unit. And to change some settings I noticed on the thermostat between hours and six and seven the unit only runs on fan mode only purchase has been taken of unit data plate and some set points on thermostat ....Homeowner would like someone to reach out to them for a plumber to check sewage lines sometime next week. Customer wants someone to reach out to them
Found furnace blower motor starting and stopping. No control voltage lost at the circuit board. Checked the wiring and the motor plug. Motor does not modulate, it stops and starts. Replaced the damaged condenser panel.
Completed the spring maintenance. Replaced air filters. Checked wiring and connections. Checked thermostat and unit operation.
Water stain on cieling shower or tub leaking Toilet leaking, replace wax ring Replace wax ring and repair toilet flange
I replaced o.d. fan motor #2 and replaced the one bad cartridge fuse. I left the other 2 I brought inside the units main electrical compartment. I turned the main breaker inside the building for unit #3 to on and let the unit cycle from the thermostat. Unit operating normal.
Installed safety switch and 4x4 junction box.
Upon arrival I found system low in R22. High Superheat, low subcool, low delta air temps. Inspected indoor and outdoor coils and found them to be clean. Filter is new and blower is clean. Quoted customer for a leak search and repair but she declined. Customer would like an soft estimate based off of current equipment size.
Upon arrival I was told that lobby unit was dripping water around counter and back clinic unit not cooling. During diagnostics I found lobby system drain pan cracked and leaking water inside of unit. Quoting customer to replace drain pan. Currently is metal, should be replaced with plastic to prevent rusting. Went to back clinical area unit and found system not running, no power. Blown fuse at disconnect. Inspected unit and found belt was broken, replaced with new, and I also found slight burn mark on condenser fan motor. Ohmed out motor and found it has open windings. Quoting customer to replace condenser motor and 3 fuses.
Spring Pm On 05/10/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter cleaned checked compressor capacitor checked EWP and LWP it was low I pump it back up to 57/50 psi also checked temp checked all other electrical connections unit tested unit operating normal at this time. recommended uv lights installation.
Mounted humidifier box
FOUND THAT THE UNIT DRAIN PAN PUMP WAS NOT OPERATING CORRECTLY. BETTER TO REPLACE THE PUMP ASSEMBLY.
Warranty call On arrival customer showed me the humidifier cavers and the panel comes out untapped the hole panel out put it back right taped with duct tape tight Up tested is working normal also highly recommended duct needs to be cleaned I gave quote for customer accepted we have to come back to Cleaning the duct 1 zone. Collected full amount of $521.90 on CC
Spring Pm On 04/23/19 the voltage absorption system was well I was recommended to the customer replaced compressor run capacitor customer approved after I finish the spring Pm I come back today with new capacitor 80UF on arrival turn off the unit replaced the capacitor I tested checked electrical connections checked voltage and amps checked all electrical connections start up and unit began operating very smoothly without any hesitating or lag measured supply and return air temp unit operating normal at this time. Collected $350.35 the credit card on file.
Spring Pm On 04/17/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced checked water pressure it was low 0 psi I pump it back up 55/50 unit tested unit operating normal at this time. Also I have to come back Tuesday04/23/19 10 to 2 to replace the capacitor.
Air Conditioning, Heating, Geothermal, And Plumbing Services In Bel Air, MD – Service, Repair, Installation, Maintenance, and Tune Up
If you are located near Bel Air, MD and you need assistance with your HVAC services, Supreme Service Today, LLC is your local community’s best provider! Our team is trained and qualified to help you with services, repair, installation, maintenance, and tune up at a moment’s notice! We have been servicing your community for years on end, and we offer the best and most affordable deals out there.
Our team is certified and trained to deal with any emergency HVAC issues, and the best part is that they are available 24/7 for all emergencies! If you have an issue that requires immediate response, we will be there in the blink of an eye any time during the day or night. At Supreme Service Today, LLC, we understand the feeling of being stuck with a system that does not work and we know the urgency that comes with getting back on your feet. Our team not only services your equipment when you need it most, but we also offer services for all different makes and models, so you can be sure that we can fix your problem, whatever it happens to be. It’s no fun living with a broken system, so make sure to get your issues sorted out right away with Supreme Service Today, LLC!
Choosing The Right Contractor To Help With Your Air Conditioning, Heating, Geothermal, And Plumbing Services in Bel Air, MD – Supreme Service Today, LLC
At Supreme Service Today, LLC, we offer the reliability and professionalism that you are looking for in an HVAC contractor. Our team is always on the move, helping customers or learning new skills to help future ones. We value continuous learning, and we make a point to take time out of our days to study and become familiar with the latest technologies and brands on the market. This way, we can better service our customers when they decide to give us a call. We are always brushing up on our air conditioning, heating, geothermal, and plumbing knowledge, and we are always prepared to deal with the unexpected.
If you need help with installations, we can help because we know all of the top brands available and can offer recommendations based on your interests and current scenario. If you need help with repairs or service, we are familiar with different techniques to identify and fix your system’s issues. And if you need assistance with maintenance or tune ups, we are always learning new ways to improve the life of your equipment. Supreme Service Today, LLC is the right choice for your heating and cooling partner because we won’t rest until you have the best experience possible. We are constantly innovating and improving ourselves because you deserve the best there is, and we want to be that for you. While we do have many top notch services that we offer, some of our basic packages include:
Emergency Repairs Any Day Of The Year
We don’t only have 24-hour availability in the case of emergency repairs, but we also are available 365 days a year for your convenience. You can bet that we will show up on time to our appointments, and we will be prepared with the right knowledge and tools to help you along with your problem. We know that around the clock availability isn’t enough to keep our customers satisfied – we also work hard to train our technicians to fix your systems in a timely manner so you are not left waiting hours on end for simple fixes to be performed. Our team will arrive at your location and be in and out before you know it! We have years of experience that have all amounted to the technical experts that we are today, and we are here to serve you when you need it most. We at Supreme Service Today, LLC are 100% dedicated to you and your satisfaction, and we will go above and beyond to keep you happy.
Keeping Your Systems Healthy With Maintenance And Tune Ups
Maintenance and tune ups can help keep your systems healthy as they fight against the passage of time. At Supreme Service Today, LLC, we can send a technician when you request an inspection to check on how everything is running. They will perform routine tests to determine the status of your equipment, fixing any small issues they find to keep your system in tip top shape. This will not only prevent these small issues from growing into larger ones, but it will also give you the peace of mind that your equipment was serviced by a licensed professional. Instead of relying on your own gut and knowledge of HVAC equipment, come to someone who has been in the business and has years of experience instead!
Alternatively, we also offer maintenance plans, where we handle the entirety of the maintenance schedule. Rather than giving us a call when you want your equipment looked at, we at Supreme Service Today, LLC will take it upon ourselves to schedule all of the inspections and visits. This way, you can completely forget about caring for your HVAC equipment and leave it up to the expert technicians on our team. You can still call for maintenance if you want it, however, and as always, you can call for repairs. All maintenance plans do is give you the option to sit back and relax as we handle all of your concerns for you!
Help Choosing A System For Installations And Replacements
If you are considering an upgrade or replacement for your current HVAC systems, Supreme Service Today, LLC can help you every step of the way. First, we can have our team evaluate your current equipment to help you determine if you actually need a replacement, or if you just need a few touch ups and repairs to stay functional. We will take many factors into account, such as the cost of repairs and the likelihood of future problems before giving you a recommendation that you can ultimately agree with or reject. If you do decide to go with a new system, our team of experts can walk you through all available options on the market that fit your requirements to help you choose one that fits your needs.
Energy Efficient Geothermal Solutions
Supreme Service Today, LLC has entered the game of energy efficient geothermal solutions for your convenience. These systems work off of energy stored in the ground, and provide a renewable source of energy that you can harness. It is an environmentally friendly solution that can keep your own needs satisfied while you care for our planet! Additionally, you can benefit from a federal tax credit if you choose to go the geothermal route. A 30% tax deduction on the cost of your installation and equipment can benefit you a lot, and Supreme Service Today, LLC can help you ensure that you are qualified to receive all benefits. If you have any questions about geothermal solutions or want to learn more about the offerings, get in touch with our experts today or visit our website!
Plumbing Services For Maximum Convenience
Supreme Service Today, LLC also offers plumbing assistance in Bel Air, MD. We believe that you shouldn’t have to go to different providers to get assistance with your home facilities, so we offer plumbing repairs, installations, and even replacements. Our team is experienced and ready to help you with whatever your needs may be! Think about the convenience of being able to call one phone number and talk to a representative you are familiar with for all of your HVAC needs in addition to your plumbing ones. Our teams are all highly trained in their specific fields as well, so you don’t have to worry about getting less value for the convenience that we offer. Our services are just as good if not better than companies who are only dedicated to plumbing matters!
All Day Emergency Plumbing Repairs
Similar to our HVAC emergency services, we take calls 24/7 for any plumbing emergencies as well. If you have anything wrong with your pipes or plumbing system, you can count on Supreme Service Today, LLC to send the right people for the job! We value responsiveness because we know that especially in plumbing emergencies, customers often can’t wait until the next day for service. We want to keep you safe and satisfied, which is why we go above and beyond to be available whenever you need us for whatever services you require in an emergency. If you work with Supreme Service Today, LLC, you will never have to worry about being left out alone when you are in need of immediate assistance.
Call Now To Get Started
The search for the perfect HVAC partner is over! Supreme Service Today, LLC is the only answer when it comes for reliable and experienced professionals providing heating, cooling, geothermal, and plumbing services, repair, installation, maintenance, and tune-up in Bel Air, MD. Get started with a provider you can trust by calling (410) 788-1144 to talk to a member of our team about how we can help you today!!