Capitol Heights, MD Air Conditioning, Heating and Plumbing Services
Supreme Service Today provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Capitol Heights, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Service Today.
for Capitol Heights, MD
Upon arrival I was shown office suite on 2nd floor. Was also shown roof access and furnace room. Ac was being called for at thermostat, went to roof and found no high voltage. Reset breaker in media room and went back to system, found no high voltage again. Went back to breaker and it was tripped. Reset but kept disconnect off. Turned disconnect on and compressor was grinding very loudly. Put gauges on and found only 30psi static pressure. Compressor needs to be replaced and unit needs to be leak searched and repaired. System is dated from 89 so Iâ€™m suggesting unit be replaced, R22 refrigerant is currently being phased out.
Completed AC inspection .
Lennox roof top unit service coral hills md