Hillcrest Heights, MD Air Conditioning, Heating and Plumbing Services
Supreme Service Today provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Hillcrest Heights, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Service Today.
for Hillcrest Heights, MD
CHARGE THE UNIT 4 LBS 410A TESTD CHECK THE UNIT CHECKED ALL ELECTRICAL CONNECTIONS. Service call on 08/23/19 On arrival set unit to call for cooling is short cycling checked electrical connections furnace checked Air filter checked drain line checked air flow measured supply and return air temp no DT checked condenser unit outdoor checked electrical connections checked compressor contractors checked compressor capacitor hold the contactor and checked pressure and temp I found is short cycling on low pressure is low on refrigerant I explained the customer gave customer quote to leak search and repair customer told me just recharge the unit for now customer thinking to replace the unit the furnace is new but the outdoor condenser unit is old and customer he is not fine the loud noise is coming out from condenser unit I gave customer another quote to recharge the unit with 4 lbs 410A and tested checked electrical connections no warranty customer accepted recharge the unit with 4 lbs an
Fall pm on 01/18/19 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter recommended air filter need to be replaced on time also the condensation pipe needs to fixed making sure no leaks I gave quote for customer she waiting until next pm unit operating normal at this time.