Jarrettsville, MD Air Conditioning, Heating and Plumbing Services
Supreme Service Today provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Jarrettsville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Service Today.
for Jarrettsville, MD
Excellent Service Person
Nau - Jarrettsville, MD
Knowledgable and polite service person! Thank you!
Response from Supreme Service Today:
Carol, thank you so much for taking the time to write this. We completely agree, Chris is excellent at providing our customers with the best of care when it comes to their HVAC needs. Our plumbers are excellent too so please keep us in mind in the event you need any plumbing services in the future. Have a supreme day!
Fall pm on 11/19/19 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked air filter cleaned checked compressor capacitor checked coil checked blower motor checked EWP and LWP checked water temp checked all other electrical connections in side the units tested units operating normal at this time. Recommended Duct cleaning uv lights installation also single or hole house surge protector installation to avoid future problems.
Fall pm on 09/20/19 on arrival set units to call for heat unit #1 it was tripped from breaker checked turned on checked electrical connections checked electrical wires checked voltage and amps measured voltage and amps no fault found checked compressor capacitor checked coil checked blower measured supply and return air temp measured EWP and LWP it was low 0 psi pump it back up to 60/55 psi check water temp unit air filter checked condenser drain and cleaned check all other electrical connections unit tested unit operating normal at this time. Highly recommended single or hole house surge protector and UV lights installation.
Customer recently replaced the filters. I checked the electrical wiring and electrical systems, all are within specification. I pressurized the ground loop to 65psi. I operated both units on second stage cooling mode and confirmed proper flow rate and heat of rejection. Unit #1, the package unit is cooling with 20+ degrees delta temperatures across the evaporator coil. Unit #2 is cooling with 18 degrees delta temperatures across the evaporator coil which is within range of printed data. I cleaned the condensate pans and drain lines and ran hot water to flush the debris and to make sure it drained properly. Both units are operating normal.
Fall pm on 02/22/19 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters is cleaned. Units tested units operating normal at this time.