Middle River, MD Air Conditioning, Heating and Plumbing Services
Supreme Service Today provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Middle River, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Service Today.
for Middle River, MD
Ron - Middle River, MD
Yonas called on his way to tell us that he would be a little early and if that was ok. Once he came in he diagnosed the system then explained what he was going to do.
Great Service and tech
Gibbs - Middle River, MD
Colin is by far your best tech. Very thorough and makes you feel very comfortable about his knowledge of his job, etc.. We had problems several months back and he was the only one who got the job done. He's a keeper.
NITROGEN LEAK SEARCH AND WATER FURNACE COIL REPAIR WITH TXV
On arrival removed defective pump. I then installed new pump ,flushed bottom section of the loop ,tested unit operation,system operating normal .customer joined our membership
Inspected 3 reznor units found unit 1 to have bad proofing switch. Unit 2 has bad blower motor. Unit 3 has bad blower motor Motors are locked up and switch is stuck open due to the switch not being the same as all the other units inducer putting out .67 wc all other unit inducers putting out .80 motor may need replacement as well if proof switch does not fix issue Waiting qoute for repair
Arrived for no heat in clinic. Inspected all units and documented in system. Tested each system in heat test mode to verify proper operations. Inspected all motors for proper rotation. Found units to be operating properly on arrival. Raised set points by one degree. Tested tstat operation running properly no issues found at this time. Completed heat season maintenance while on site. Changed all filters and belts. Tested all units and documented all finding found all units to be heating properly.
Replaced the air coil and charged unit with 8lb12oz of r410a refrigerant after pressurizing and checking for leaks and pulling into a <500 micron vacuum. We also replaced the left pump. The right pump makes a slight noise but itâ€™s performance isnâ€™t effected. I will let the office know to cancel follow up call to replace the left pump. Unit operating normal. Customer paid balance for air coil replacement and remaining balance of loop pump replacement. Job paid in full.
Helped Chris remove and reinstall Evap coil on packaged system, was here for about 3 hours. Stayed until he started vacuum to verified it isnâ€™t leaking. While vacuum was being pulled he put unit back together while I replaced pump. Chris is staying behind to finish and will collect from customer.
On arrival found one pump is over amping and the other is making loud noise ,recommended replacing both .added some refrigerant until we get the coil .unit is operating on one pump . Need to order an order pump .
Up on arrival performed fall maintenance inspection on 12/02/2019. Checked all thermostats for operation, checked all units for operation. Took delta T on all systems. Checked all electrical components on all systems. Changed all air filters ( 8 - 20x24x2 ) changed all belts ( A-53 ) . All systems operating normal at this time.
The right pump is locked and needs to be replaced. However I found refrigerant oils heavily accumulated in the condensate pan because the heat of extraction was less than 2 degrees. The air coil is visibly leaking refrigerant from a place that cannot be mechanically fixed and must be replaced. I called the customer who is not home and explained this to them as well as the membership benefits. Customer will call the office on Monday to make a payment and approve the repairs. Unit is operating on auxiliary heat. I did pull 24volts to the compressor contactor because the unit is zoned and kept bringing on the compressor.
Service call on 11/25/19 on arrival I see error codes on thermostat I checked the unit checked electrical wires checked electrical connections checked compressor capacitor checked coil reset the unit set the unit to call for heat when the unit is comes on I hard noise from left side water pump also checked EWP and LWP it was 0 psi also checked water temp I suggested to replace the water pump I gave quote for customer also I gave customer-$50 hvac service discount customer accepted the quote I ordered the pump we have to come back to finish the job unit turn off from the breaker. Collected $638 for job deposit on C.C. WATER PUMP REPAIR
Saddle valve is leaking
RECHARGE THE UNIT 4 LBS 410A NO WARRANTY AND REPAIR COMPRESSOR CONTACTOR Service call on 09/19/19 On arrival set unit to call for cooling the geo water furnace split has error code low pressure led on checked water pressure checked electrical connections checked compressor capacitor checked voltage and amps measured supply and return air 8 degrees DT checked coil is cleaned checked blower motor cleaned checked all other electrical connections reset the unit the low pressure/comp error codes move set the unit to call for cooling checked electrical connections checked voltage and amps measured supply and return air still 8 digress DT checked EWP and LWP 35/30 psi checked water temp 63/69 checked pressure and temp I found the unit low on charge 410A I explained the customer what I found and I gave the customer quote options to search the leaks and to recharge the unit customer accepted to recharge the unit with 4 lbs 410A also I suggested to replacing the compressor contactor to avoid fu
Performed Operational Inspection. Checked in with receptionist, they said units have been working great without any problems. Went to roof, customer gave me ladder code but it didnâ€™t work, had to set up ladder. Replaced all filters. Flushed out drains. Checked cleanliness of coils. Belts in good condition. Checked capacitors and contactors, tightened electrical connections. Ran ac on both units. Measured delta air temps. Measured amp draw of compressors, od fans, and blowers. Only issue I found was unit 2 had OAT and SAT sensor faults. Found plug slipped out of control board, plugged back in and faults went away. Units operating normal at this time.
Up on arrival performed fall PM , checked units . All components are in good condition and operating perfect . Both condenser coils needs to be cleaned
Upon arrival spoke with customer was told he was experiencing a back up at the city/county connection. Advised to call county to check there side of the main line. Also was advised to look at another side branch line running through business.was told that he had another plumbing company try to snake it but couldnâ€™t go any further then ten feet. Advised that we should camera the line since itâ€™s cast iron just to find out the condition of pipes. Then will snake it if no issues were found
On arrival, completed approved repairs, replaced compressor wire harness, replaced contactor, and repaired damaged wires. Turned system back on and itâ€™s running and cooling.
Upon arrival found fan had slid down on shaft, this had caused abrasions on insulation to two fan motor wires, cut 1 fan motor wire (both repairable damage), and wrapped two compressor wires around fan. The wrapped wires tore out of contactor (damaging contactor) until twisting and warping wire so tight that it tore them apart. Insulation has been damaged on compressor wire beyond repair. Customer has approved repairs where we will replace compressor wire harness with new wire harness and wire, repair damaged fan motor wires, and replace damaged contactor. Deposit for work has been taken today, $327.50.
On arrival found drain clogged cleaned it ,tested it ,unit draining properly
Completed the spring maintenance. Cleaned the condenser coils. Cleaned the drain pans and traps. Checked the wiring and connections. Checked blower belts. Checked unit operation.
Upon arrival found system off and aux pan full of water. Customer informed me had recently changed filter, filter was very dirty. Vacuumed out aux pan and tried to test system. Outdoor system did not come on, traced electrical problem back to breaker panel. No voltage out of breaker. Turned breaker all the way off and back on and system came on, checked all electrical components to make sure nothing was shorting causing the breaker to have tripped. All components good. System cooling properly. Upon wrapping up with customer was informed customer was testing system from breaker panel when troubleshooting before arrival.
On arrival found system low on refrigerant.explained to custOmer that system lost refrigerant due to a leak somewhere. Customer approved recharge.recharged system with 410a ,SUbcool 15 degrees .unit operating normal at this time .
Service call on 06/01/19 On arrival set unit to call for cooling outdoor unit is running but the indoor fun motor is not checked electrical connections checked voltage and amps checked 24v I found the ECM MOTOR is not running the motor is bad I gave quote for customer but customer he donâ€™t want to repair he have house warranty unit is not operating at this time. Collected $129 trip fee and $116 for diagnostic fee total $245 on CC
Found condenser fan motor grounded. Install a new fan motor. Made all wiring connections. Checked operation. The unit is R22 refrigerate. Customer would like a price on a new unit.
Performed ac pm on Geo System. Replaced provided filter. Flushed out drain line, pan, trap. Inspected coil and blower. Checked capacitor and contactor. Tightened electrical connections. Ran both stages of ac. Checked delta air temps at Evap coil. Measured delta loop pressures and temps. Measured amp draw of compressor, blower, loop pump, and Dhw pump. Checked Dhw operation. Unit is operating normal at this time. Customer is moving to Havre de Grace so I informed them to call the office when they do if they would like service on hvac Equipment.
I cleaned the condensate pan and drain lines and ran water to make sure it drained properly and that the condensate pump was working. Filter was recently replaced. I checked the electrical wiring and electrical systems, all are within specification. I let the unit run for 10 minutes on cooling mode and only had 16-17 degree delta temperature across the evaporator coil. I put my gauges on the system and had 20-22 degree superheat. I tightened valve stems and used electronic leak detector to make sure there were no system leaks, then added 10oz of r40a refrigerant to obtain 23 degree delta temperature and 7-9 degree superheat. Unit operating normal. System less than 1 year old.
Upon arrival I spoke with manager inside who called building management company and got the roof ladder code. Went to roof and uploaded equipment info. Gave office filter and belt sizes. Went to supply house and picked up filters and belts. Returned to replace filters and belts. Inspected coils and blowers. Checked capacitors and contactors. Tightened electrical connections. Ran heat and checked operation. Measured heat rise and amp draw on both units. Let systems satisfy thermostats. Both units operating normal at this time.
Upon arrival I was told that thermostat was fluctuating in temp and customer wasnâ€™t sure if Geo was working properly, when switched to emergency heat system satisfied relatively quickly. During diagnostics I found Geo running at first stage but fan speed running at max capacity, which was lowering output and made system run too long, making loop cold. Rewired board for LoY and Y2 so fan runs at proper speed for both stages. Then I found adaptive recovery on for thermostat, turned off. Finally I increased compressor lockout from 15 degrees to 30 degrees. Informed customer to keep emergency heat on for today because loop is cold and is affecting performance. Turn Geo back on tomorrow, loop needs to warm up. Unit operating normal at this time.
The White Rodgers thermostat was dropping voltage when it tried to run 2nd stage compressor heat mode. I showed the customer what was going on so they could understand the problem. I charged the unit to specification in first stage because it never would go into 2nd stage last week. The old thermostat had no test mode either. I did not suspect any refrigerant problems when I put my gauges on. I checked heat of extraction was at 40,000 btu which was above printed material of 35,700. Temperature rise more than 30 degrees. I took a picture of the measurements. I installed lyric thermostat. I ran into a problem because the outdoor temperature sensor was three wire. I had to replace with Honeywell 2 wire. Unit operating normal.
Service call on 01/21/19 On arrival the condensation pump keep running also the pan full of water the problem was the condensation tube frozen up no water going out I run the tube to the washing drain line in side the house checked electrical connections tested unit operating normal at this time. Everything under warranty no charge.
There is evidently a pin hole in the evaporator coil. I saw traces of oil on the pan under the coil. I mentioned coil replacement as an option but customer and I agreed that using internal leak sealer and recharging is a better option. I added the leak sealer and charged the system until it matched printed specification data and had normal operating pressures and temperature rise and heat of extraction as well. Unit operating normal.
Found unit without power . We found the breaker and turned it on . Unit has power of 118 volts . Checked operations and system is operating ,
Replace Inducer Motor and Assembly, belt and filters on carrier unit. Customer gave me gate code 3562 and door code 0232 and said he would meet me there. Upon arrival I went to roof and shut off power. Removed inducer Assembly and Wiring. Sanded down metal with old seal for clean surface. Installed new inducer Assembly with seal. Secured to panel and wired to unit. Replaced 4mfd run capacitor. Returned power to unit and jumped out heat. Removed jumper and replaced filters and belts. Ran Heat from thermostat and checked operation. No other problems found. Unit operating normal at this time. Customer not on site, did not sign.
Replaced water heater suspended in the ceiling , 6 gallon electric W/H
Upon arrival I went to RTU and could hear incuder running, no flame, blower not running. Opened up panels to find system faulted on inducer fault yet inducer is running. Shut off power and checked specs. Found capacitor out of spec. Put new one on to test but when starting unit I noticed inducer started right away but was running strange. Checked voltage and only had 200volts, needs 480v. Then thermostat called for heat and inducer started running at full capacity. Removed call for heat and inducer kept running but was making some noise and started to smoke. Ohmed out motor terminals and found we have a short in the inducer motor, making it run 24/7 and at lower voltages. When only supplied 1 leg of power, the inducer tries to run and is shorting out. Verified tha board is sending out correct voltage and operating normally. Need to replace inducer Assembly. Also found belt is very worn and filters are very dirty. Also checked heat exchanger, didnâ€™t find any cracks but can see a decen
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked filter,coil,safeties ,cap was low and blower was dirty .unit is operating normal at this time
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked coil,cap ,heat exchanger.found blower dirty and cap below manufacturer specs.unit operating normal at this time .
Took off $25.50 because I messed supply line and is lookin for some new ones to install. Have to come back to install new supply line..