Randallstown, MD Air Conditioning, Heating and Plumbing Services
Supreme Service Today provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Randallstown, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Service Today.
for Randallstown, MD
Service call on 11/13/19 On arrival customer thermostat has error codes AWL-3 aurora web link communication error it was enable from thermostat desable it the communication from the thermostat reset the unit call for heat and cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked condenser drain checked air filter checked water temp and water pressure unit tested unit operating normal at this time. No payment collected is under warranty.
Toilet leaking from missing upper tank bolt to tie to toilet bowl. Also found the inner works of the toilet to be very rusted and old would recommend replacing the whole toilet.
Up on arrival found bad capacitor, installed new capacitor checked unit for operation, unit operating normal at the moment, Recommended hardstart kit and membership customer declined
Upon arrival I met Allied technicians and they showed me the job. Shut off power to the Geo and removed cooling tower from system. Disconnected wires and hoses then ran hoses to flow center. Tightened with double clamps then insulated hoses and fittings. Finished by wiring both flow center pumps to the system. Once Allied technicians were finished piping to the top of flow center then flushed the loop with flush cart. They then informed me that they donâ€™t have insulation to finish insulating lines from wall penetration to flow center. They also said they need to return to add ethanol to loop. Once flush was finished we turned the system on to test it. Waited for Ryan to get here and then we put the cooling tower in his van. Put the box of extra materials in my van to bring back to shop. Finally I set up system with aid tool and answered any questions he may have. He only asked us to follow up on an outdoor temperature sensor. Does it come with his system for aux heat lockout? If not,
When I arrived, at 6:22p.m I checked and charge unit with 410A Freon 1lb. Customer is thinking about getting membership. Dealt T is 55*
On arrival found system low on refrigerant,possibility of a leak .customer choose to recharge it at this time . I added 1lbs of 410a .unit operating normal at this time.
On arrival found coil frozen .advised customer to reschedule
Upon arrival I was told that customer turned ac on but system wasnâ€™t blowing out cold air. During diagnostics I turned on ac from thermostat and found everything turned on properly but when I got to the condenser I found cover was still wrapped around unit, restricting all air movement. Removed cover and let system run. Found normal operation. Told customer to keep cover off when running ac in the summer. Only cover unit after cooling season is over and you donâ€™t need to run it anymore during the winter. Customer refused to pay. Office please follow up, he said he would like to speak with Alex if possible.
On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain,coils,caps,blower ,unit operating normal
Customer has leak in diverter need to be replaced customer will try to use universal repair kit from Home Depot then call back if it doesnâ€™t work
Donna called Mel and we need to double check if we are servicing this location
Me and cameron removed water heater from basement
Replaced 50 gallon power vent water heater in basement , installed new valve expansion tank and pan , tested no leaks , basement had flooded and all the furniture is wet covered in mold and in the way of the steps was able to slide new heater over in a box was unable to do the same with the old heater customer has a mold remiadation company coming to clear basement will call back in when itâ€™s clear enough to remove old water heater