Sykesville, MD Air Conditioning, Heating and Plumbing Services
Supreme Service Today provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Sykesville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Service Today.
for Sykesville, MD
Tom - Sykesville, MD
Yonas, did a great job. No complaints at all. Very seldom do I rate anything Excellent. But as I said Yonas did a great job - explained everything he was doing. plus made recommendations on some maintenance item and why
Response from Supreme Service Today:
Good morning Tom! We appreciate you taking the time to leave an amazing review about your experience with Supreme Air! we look forward to working with you in the future! Thank you for being a Supreme member!
Passed inspection When tile and drywall are done, we need to return for trim out and final inspection to be called
LP power vent water heater replacement estimate. Once replaced I tested and no leaks were found. Water heater is up and running.
Got bathroom ready for inspection
Pipe in a shower pan and tub for drain lines and water lines and diverters for both showers. Tie into 3 inch drain line and lead a new 2 inch line over for both showers. Take in a studor vent above the vanity drain line do give proper venting on tub and shower pan. Today I set tub and got materials
Gave estimate for work to be preformed. Will return in morning to start the work to be preformed for the bathroom remodel.
Inspected system found drain line freezing up. Warrenty to installation per Colin. Ran new rain line hose to indoor sump drain. Zip tied and tested unit now running properlly.
Service call on 12/20/19 On arrival customer explained to me what happened in the morning the furnace is not operating the house temp 60 degrees customer set the thermostat 70 degrees unit is not running round 1 pm the unit is comes on by his self and after customer told me I set the unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections turn the unit off checked the ignitor homes checked the flame sensor checked the blower motor checked inducer motor checked pressure checked the flue pipe checked the filter checked gas pressure tested run the unit multiple times no error codes unit operating normal I call tech support they cannot help us on this point bc the unit operating normal I explained the customer she had to call us back when the unit doesnâ€™t work if happens again . Customer unit under warranty we installed the unit 05/20/19 no charge for this trip. I explained about the service agreement customer sign new service
Return visit on 11/20/19 On arrival checked the unit is geo water furnace package already has condenser drain sensor we canâ€™t build another On also customer has water sensors around the unit customer he is not happy last technician is here do service for him.I do fall pm set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked air filter checked blower motor checked coil checked EWP and LWP checked water temp checked all other electrical connections unit tested unit operating normal at this time. No ez trap installation No payment collected customer paid deposit for Ez trap installation but customer wont that money toward to maintenance service.
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections inspected water pressure,Contactor,coils,filter,safeties ,unit operating normal
Up on arrival performed fall maintenance on 10/31/2019. Checked thermostat for operation, checked system for operation. Changed air filter. 28x30x2 . Took delta T, delta P. Took readings of electrical components. Unit working good at this time.
Up on arrival performed fall maintenance. Checked thermostat for operation, checked unit for operation. Took delta P , delta T , changed filter. Unit working properly at this time
Came back to install 1â€male cpvc adapters to carbon filter base. Shut down well pump. Restarted pump and tested connections. No leaks were found. Well be quoted the estimate and billed in a 30 day bill payment system. Has an open balance for this already. Will just need to be billed.
Cut in ball valve before filter and replace gage on tank tee After testing system found leak on male adapter going into filter need to return and replace male adapter that has been glued into filter parts needed 2 1â€ male adapter cpvc x stainless ,1 1â€coupling cpvc 3â€™ 1â€ cpvc
Upon arrival found faucet clogged due to well water cleaned the screen and it worked fine after that. Checked other faucets while here. Also took a water sample for Alex to test an see either another option for salt or filtration system for water treatment.
Found a mouse nest in the electrical compartment. Cleaned out the nest. Found the capacitor blown and the contactor burned. Replaced both components. Made all wiring connections. Checked the refrigerate charge. Checked operation.
On arrival set units to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections inspected drain and cleaned it ,inspected water pressures,coils,caps,contactors ,filters .units are operating normal at this time
Installation of Amana Heat Pump System Heat Pump M# ASZ160241 S# 1904298826 Air Handler M# ASPT29B14 S# 1904133604
Spring Pm On 05/31/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced checked compressor capacitor checked all other electrical connections unit operating normal at this time.
Replace shower diverter with new one.
Install customer supplied vanity and faucet in first floor hall bath customer has vanity picked out and paid for asked us to pick up from Home Depot in randallstown customer will send over info for pickup
Spring Pm On 05/02/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter cleaned checked EWP and LWP also temp checked compressor capacitor I was recommended replacing contactor customer accepted quote replaced the contactor checked electrical connections checked voltage and amps I tested start up and unit began operating very smoothly without any hesitating or lag unit operating normal at this time. Collected $150 balance on CC on file.
Customer gave deposit of $263.92 on 4/22/19 to install vanity faucet is scheduled to arrive on Wednesday 4/24/19 will call to schedule when it arrives
Spring Pm On 04/08/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter is cleaned checked capacitor checked EWP and LWP psi unit tested unit operating normal at this time. Recommended UV lights installation
To replace sump pump and battery back up sump pump system in back sump pit To cut open wall behind the upstairs shower and install a Moen Adler single handle diverter , will also replace drip ear elbow as the shower arm snapped in the elbow customer responsible for all drywal repairs To cut out and repipe kitchen sink and dishwasher drain from the tailpiece to the wye for dishwasher and the trap as well will use fernco to connect to existing pipe To cut out make hole bigger in concrete foundation to install new frost proof hose bibs , one on side 4â€ frostproof , also the front one with an 8-10â€ frostproof hosebib Cut out abs pipe for kitchen drain under sink. Replaced trap also repiped the branch line for dishwasher Replaced hose bib out front and back of house with frostproof hose bib - copper is leaking from old 90 and running down pipe will need to cut out pvc drain for sump and replace the copper 90 then repair the pvc Pulled sump pump system out of pit , installed new rig
Customer paid $1578.00 deposit on work to be done ,would like Thursday to complete work , check did scan will bring to office
Replace 38 gallon electric water heater in basement need install ball valve expansion tank and pan
Need to return to install 36 gallon lowboy electric water heater
On arrival we checked thermostats. We inspected both of the water furnace(7 series and 5 series). We inspected capacitor, thermostat connections, contractors, LWP,EWP,EWT,and LWT. After finishing with the inspection we waited for the system to start running. Units are operating normal.
I replaced the filter with one provided by the customer. I operated the unit in second stage and auxiliary stage heating mode. I reset blower high speed from 8 to 7 to increase the temperature rise to 25 degrees. I confirmed proper flow rate and adequate loop pressure as well as heat of extraction. I checked the electrical wiring and electrical systems, all are within specification. The unit is operating normal. I am sending the customer an estimate to install a humidifier.
I operated the unit on second and auxiliary heat stages. Increased blower speed in auxiliary heat stage to decrease temperature rise. I confirmed proper flow rate and heat of extraction. Ground loop pressure holding within recommended range. I checked the electrical wiring and electrical systems, all are within specification. Zoning is operating as intended. Unit operating normal.