Woodstock, MD Air Conditioning, Heating and Plumbing Services
Supreme Service Today provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Woodstock, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Service Today.
for Woodstock, MD
Upon arrival customer showed me condensate line that exits furnace is leaking. Pulled on pvc 90 and it came right out of grommet. Cut off 90 to find adapter was installed backwards and short end cannot be clamped because it isnâ€™t long enough. Used extra drain cpvc that was left over to connect to grommet, slid pipe in enough so it could be clamped, then used pvc 45 to connect to drain line. System isnâ€™t leaking anymore but drain configuration isnâ€™t right, we need correct fitting for pvc 90 to connect to furnace drain.
When I arrive customer told me this job and can be difficult to light the pilot on the furnace it can take up to 2 to 3 hours to do so I began to follow the steps to light the pilot on the furnace pilot will not light but will light on the word set but the flame will go back out again I was unsuccessful of lighting the pilot on the furnace. I gave customer two options of replacing gas valve and igniter and orifice. Customer is going to get a company to fill her propane tanks up to take a look at it if they canâ€™t get a light sheâ€™s thinking about getting furnace replace this happens twice a year.
Arrived onsite to repair filter door not closing properly.inspected unit and found door to need new screws installed and to be crimped to hold better. Placed door back on with new bolts. Removed washable filter for customer since she wants to use replaceable ones. Warranty per Alex.
Upon arrival added 4 lbs 6 oz to system. System now operating with 325 psi (high) 125 psi (low) 8 degrees of sub cooling, 14 TD on outside coil and 18 TD on inside coil.
Installed bathroom faucet pop up assembly drain valves and escutcheons installed trim kit for shower still need to install slider rod and toilet wall is not painted yet to install toilet also kitchen floor is not finished and cabinets are not installed to complete trim will need to return once painting flooring and cabinets are installed and appliances are here to hook up and test
Customer had no water to home found water service line under trailer not buried but insulated and wrapped with heat tape plug had come loose for heat tape causing line to freeze once heat tape was back on line thawed and water was restored to home
To cut and repair broken cpvc pipe in ceiling Replaced split cpvc line in basement ceiling , customer had another plumber out last night who made the top connection also cpvc is very very brittle from well water and age would highly recommend a repipe at least going up to the kitchen also need to insulate the back wall as there is no insulation up high and itâ€™s noticably freezing cold in the bay.
On arrival found system locked on pressure switch ,I then reset system ,unit came back on,checked pressure ok.checked exhaust motor which was rated for .75 and actual was .8 amps,motor was hot to touch .also pressure switch kept opening ,unit is 15 years .needs pressure switch and exhaust motor. .unit is in bad shape better to replace
No heat on a Miller furnace in Woodstock , Md .